Holtec HI-STORM UMAX canister storage systems and all other thin-wall nuclear waste canister storage systems are vulnerable to short-term radioactive leaks and potential explosions and criticalities. Thin-wall canisters have the following design flaws:
- Vulnerable to short-term cracking and major radioactive leaks
- Cannot be inspected inside or out
- Cannot be repaired
- Cannot be monitored or maintained to PREVENT radioactive leaks.
Holtec admitted to the NRC that if fresh (unborated) water enters the canister a criticality can occur. The NRC confirmed this. They claim it won’t happen stating there is insufficient humidity at the Pacific Coast for moisture to dissolve marine salts on the thin-wall canisters. They admit moisture with salt is one of the major known triggers for cracking of stainless steel containers. They ignore Pacific Coast weather conditions of frequent fog and on shore surf as shown in the photo below of San Onofre shrouded in fog. They ignore their own evidence of similar components at San Onofre having cracks and leaks from moist salt air.
- Holtec Response to First Request for Additional Information (RAI) for HI-STORM UMAX Canister Storage System (TAC No. L24664), January 30, 2013 (ML13032A008)
- Criticality Comments Docket NRC-2016-0238-NUREG/CR 2214 Aging Mgmt MAPS
In the Spent Fuel Pool environment, the minimum critical volume necessary to sustain a nuclear chain reaction (criticality) may be as small as four fuel assemblies (ML16097A169). Canisters contain 24 to 37 PWR fuel assemblies.
There are no approved or adequate plans to deal with cracking or leaking canisters. Listen to this audio recording where this and other Holtec MPC canister issues are discussed at the 9/28/2017 Holtec and NRC public meeting.
- The thin-wall (1/2″ to 5/8″ thick) stainless steel canisters are vulnerable to short-term stress corrosion cracking.
- The below ground concrete structure (with air vent lids) only has a 10-year warranty from Holtec. The thin-wall steel canisters have a 25-year warranty that is void if the concrete structure fails after 10 years.
- Canisters with even partial cracks cannot be transported according to NRC Regulation 10 CFR § 71.85.
- The Koeberg nuclear plant had a similar container (a tank) leak in only 17 years. Koeberg cracks up to 0.61″ deep are thicker than existing Holtec canisters (0.50″). The NRC states both 304/304L and 316/316L stainless steels (SS) have the same vulnerabilities. The Koeberg tank was 304L SS.
- Holtec promised to use 0.625″ thick canisters at San Onofre. However, their NRC license is only approved for 0.50″ thick canisters.
It’s not practical to repair a damaged canister, says Dr. Kris Singh, CEO, Holtec International.
“…It is not practical to repair a canister if it were damaged… if that canister were to develop a leak, let’s be realistic; you have to find it, that crack, where it might be, and then find the means to repair it. You will have, in the face of millions of curies of radioactivity coming out of canister; we think it’s not a path forward…
…A canister that develops a microscopic crack (all it takes is a microscopic crack to get the release), to precisely locate it… And then if you try to repair it (remotely by welding)…the problem with that is you create a rough surface which becomes a new creation site for corrosion down the road. ASME Sec 3. Class 1 has some very significant requirements for making repairs of Class 1 structures like the canisters, so I, as a pragmatic technical solution, I don’t advocate repairing the canister.”
Instead Dr. Singh states
…you can easily isolate that canister in a cask that keeps it cool and basically you have provided the next confinement boundary, you’re not relying on the canister. So that is the practical way to deal with it and that’s the way we advocate for our clients.
However, there are many problems with Dr. Singh’s solution of putting cracked and leaking canisters inside [transport] casks.
- There are no NRC approved Holtec specifications that address Dr. Singh’s solution of using the “Russian doll” approach of putting a cracked canister inside a [transport] cask.
- NRC requirements for transport casks require the interior canister to be intact for transport high burnup fuel. This NRC requirement provides some level of redundancy in case the outer cask fails. Does this mean this leaking canister can never safely be moved? Who will allow this to be transported through their communities? How stable is the fuel inside a cracked canister?
- What is the seismic rating of a cracked canister (even if it has not yet cracked all the way through)? The NRC has no seismic rating for a cracked canister, but plans to allow up to a 75% crack (IWB-3640). There is no existing technology that can currently inspect for corrosion or cracks. The NRC is allowing the nuclear industry 5 years to develop it. It is likely to be inadequate due to the requirement the canisters must be inspected while in the concrete overpacks.
- What is the cost for the transport casks that will be needed for storage? Will they be on-site? Where is this addressed? Transport casks are intended to be reusable because of their higher cost. How and where will they be stored and secured on-site?
- How will the leaking canisters be handled by the Department of Energy at the receiving end of the transport? The DOE currently requires fuel to be retrievable from the canister.
A better solution is to use thick casks that are not susceptible to cracks, that can be inspected and repaired and that have early warning monitoring systems that alert us before radiation leaks into the environment. This is what most of the rest of the world uses. Learn more…
Holtec obtained a license amendment to use the Holtec HI-STORM UMAX system in high seismic areas effective September 8, 2015. However, it’s not approved for any specific site, including San Onofre; that requires additional approvals, and they are only certified safe for 20 years. Any issues that may occur after 20 years are not considered by the NRC, even though they know they must last for decades and they do not have aging issues resolved. See more details below.
Letter To Coastal Commission regarding Holtec UMAX NRC approval, September 18, 2015, outlines the limitations of the approval, including the following items:
- Not an approval for use at San Onofre. “This rulemaking makes no determination regarding the acceptability of this amended system for use at any specific site.”
- Certified for only the initial 20 years. Any evaluation for conditions that may occur after this [such as cracking, inspection, aging management, fuel cladding failure from high burnup fuel] are outside the scope of this approval. “Long-term” [as referenced in the Holtec Safety Evaluation] is a general descriptive term that is not required to support any regulatory or technical evaluation, and thus is not required to be more formally defined.
- Excludes any plan for storing failed (cracking) canisters. Both San Onofre V.P. Tom Palmisano, and Holtec President, Dr. Kris Singh, state transfer casks can be used to store failed canisters (July 23, 2015 Community Engagement Panel meeting). However the NRC states “The HI-STORM UMAX transfer cask is authorized to transfer intact canisters [e.g., not cracking or otherwise failed canisters].” “Implementing corrective actions in the event of a failed MPC [multi-purpose canister] is the responsibility of the general licensee and those corrective actions are not incorporated into CoC [Certificate of Compliance] No. 1040.”
- Approved only for 0.5” thick canisters – not the 0.625” thickness San Onofre proposes. “The nominal MPC thickness for the canisters certified under CoC No. 1040, Amendment No. 1 is 0.5”. The NRC has no knowledge of a Holtec proposal to increase the thickness of an MPC to 0.625”. If presented with an amendment request to do so, the NRC will evaluate it in accordance with 10 CFR part 72 requirements.”
- The underground system evaluated is different than the system proposed for San Onofre. The approval is for an underground system, not the partially underground system proposed for San Onofre. “Pursuant to the regulatory requirements in 10 CFR 72.212(b), any general licensee that seeks to use this system must determine that the design and construction of the system, structures, and components are bounded by the conditions of the CoC by analyzing the generic parameters provided and analyzed in the FSAR [Final Safety Analysis Report] and SER [Safety Evaluation Report] to ensure that its site specific parameters are enveloped by the cask design bases established in these reports.”
Other problems with the experimental UMAX system
- The UMAX system does not have drains.
- Water and other debris can enter through the air vents.
- The Final Safety Analysis specifications state hoses must be inserted in the air vents to remove water and other debris. See diagrams below.
- Air vent ducts are not required to be inspected as long as temperature is within range. “For VVMs [vertical ventilated module holes] with installed temperature monitoring equipment, verify that the difference between the average VVM air outlet duct temperature and ISFSI ambient temperature is ≤ 87 degrees F for VVMs containing MPC-37s and ≤ 85 degrees F for VVMs containing MPC-89s. Frequency 24 hours.” ML16341B100 PDF Page 26 or Page 3.1.2-2
- The UMAX system is unproven, significantly more costly and unlikely to have costs reimbursed from the Department of Energy, states Entergy VY (Vermont Yankee) in their rejection of the Holtec underground system.
…therefore unlikely that the cost of a spent fuel storage system that is significantly more costly than another available alternative can be recovered from DOE. Entergy VY continues to believe that the HI-STORM 100U [UMAX] system not only would be significantly more difficult and substantially more expensive to install than the above-ground HI-STORM 100 system, but also carries significant schedule and cost risks associated with an unproven system.
Petition of Entergy Vermont Yankee for Second Independent Spent Fuel Storage Installation Supplemental Prefiled Testimony of George Thomas, Vermont Public Service Board, PSB Docket No. 8300, May 11, 2015, page 8
Holtec HI-STORM UMAX Technical Specifications Amendment 2
- ML16341B061 – Holtec HI-STORM UMAX Canister Storage System Amendment 2, January 6, 2017 webpage (San Onofre uses this Amendment 2)
- ML16341B077 – Letter to K. Manzione re: HI-STORM UMAX Canister Storage System Amendment Request No. 2 (CAC No. L25007). (3 pages), 1/6/2017
- ML16341B080 – Enclosure 1: CoC No. 1040, Amendment No. 2, Letter to K. Manzione re: HI-STORM UMAX Canister Storage System Amendment Request No. 2 (4 pages), 1/6/2017
- ML16341B100 – Appendix A: Technical Specifications, Letter to K. Manzione re: HI-STORM UMAX Canister Storage System Amendment Request No. 2 (38 pages), 1/6/2017
- ML16341B107 – Appendix B: Approved Contents and Design Features, Letter to K. Manzione re: HI-STORM UMAX Canister Storage System Amendment Request No. 2 (54 pages), 1/6/2017
- ML16341B129 – Enclosure 2: Safety Evaluation Report, Letter to K. Manzione re: HI-STORM UMAX Canister Storage System Amendment Request No. 2 (8 pages), 1/6/2017
- Final Safety Analysis Report (FSAR) HI-STORM UMAX Canister Storage System Revision 3, June 29, 2016 (ML16193A339) (San Onofre uses this revision)
Holtec HI-STORM UMAX Technical Specifications Amendment 1
- Holtec International HI-STORM UMAX Canister Storage System, Certificate of Compliance No. 1040, Amendment No. 1 Direct Final Rule, Federal Register Vol. 80, No. 173, pp 53691 – 53694, effective September 8, 2015
- Certificate of Compliance No. 1040, Amendment No. 1 for the HI-STORM UMAX Cask Storage System, September 8, 2015 (ML15252A426)
- Appendix A of Proposed Technical Specifications ML15070A153
- Appendix B of Proposed Technical Specifications ML15070A152
- Preliminary Safety Evaluation Report (SER) ML15070A149
- Request for Amendment Application dated July 11, 2014 ML14202A029
- Submittal of HI-STORM UMAX Canister Storage System Certificate of Compliance No. 1040 Final Safety Analysis Report. (8 page(s), 7/11/2014) ML14202A030
- Attachment 1 to 5021022 – HI-2115090, Revision 2, “Final Safety Analysis Report On The Hi-Storm Umax Canister Storage System”. (630 page(s), 7/11/2014) ML14202A031 [pdf p. 241: MPC-37 dimensions: 213” (max length fuel) x 75.75” outside diameter, upper lid thickness 4.5”, lower lid thickness 4.5”, shell thickness 0.5”, baseplate thickness 3.0” [per Randall Granaas at SCE, length of MPC-37 at San Onofre is 201.5″].
- NRC Requests for Additional Information (RAI)
SCE documents to the Coastal Commission for Application to install Holtec UMAX system
- Attachment A Project Description 02182015
- Attachment B Environmental and Land Use Issues 02182015
- Attachment C Figures 2-17-15
NRC approves experimental heat levels in Holtec thin-wall canisters
- Holtec did not provide sufficient proof the Holtec MPC-37 and MPC-89 canisters can hold equal or greater than 30kW heat loads. However, rather than disapproving this, the NRC is allowing this to see if it works, experimenting with our safety. If they are wrong, this could damage the fuel assemblies, but they won’t know unless there is a criticality, because the canisters are welded shut. [Existing San Onofre Areva NUHOMS 24PT4-DSC thin-wall canisters were loaded with a maximum temperature of 15.39kw. Technical specifications allowed up to 24kW.]
- The NRC requires Holtec to have the ability to return fuel from dry storage canisters to a pool or dry fuel handling facility (hot cell), but they only require them to demonstrate this with a mockup dry-run: “a dry run HI-STORM FW MPC Storage System unloading, including flooding MPC cavity and removing MPC lid welds. (A mockup may be used for this dry-run exercise.)”
- ML16280A017 – Enclosure 1: CoC No. 1032, Amendment No. 2 [Letter to K. Manzione re: Issuance of Certificate of Compliance No. 1032, Amendment No. 2 for the HI-STORM Flood/Wind Multipurpose Canister Storage System]. (4 page(s), 10/25/2016)
8. SPECIAL REQUIREMENTS FOR FIRST SYSTEMS IN PLACE
For the storage configuration, each user of a HI-STORM FW MPC Storage System with a heat load equal to or greater than 30 kW shall perform a thermal validation test in which the user measures the total air mass flow rate through the cask system using direct measurements of air velocity in the inlet vents. The user shall then perform an analysis of the cask system with the taken measurements to demonstrate that the measurements validate the analytic methods described in Chapter 4 of the FSAR. The thermal validation test and analysis results shall be submitted in a letter report to the NRC pursuant to 10 CFR 72.4 within 180 days of the user’s loading of the first cask with a heat load equal to or greater than 30 kW. To satisfy condition 8 for casks of the same system type (i.e. HI-STORM FW casks), in lieu of additional submittals pursuant to 10 CFR 72.4, users may document in their 72.212 report a previously performed test and analysis submitted by letter report to the NRC that demonstrates validation of the analytic methods described in Chapter 4 of the FSAR.
- Issuance of Certificate of Compliance No. 1032, Amendment No. 2 for the HI-STORM Flood/Wind Multipurpose Canister Storage System (TAC No. L25005). Accession Number: ML16280A008 , Released: November 1, 2016 (package of documents)
NRC approved a 20-year general license for the UMAX system April 6, 2015 for lower seismic risk areas.
- Federal Register Notice List of Approved Spent Fuel Storage Casks: Holtec International HI-STORM Underground Maximum Capacity Canister Storage System, Certificate of Compliance No. 1040, Docket NRC-2014-0120, March 6, 2015
- Comments submitted by San Onofre Safety and others regarding the Holtec UMAX.
- Other comments submitted on Holtec UMAX
- NRC Certificate of Compliance No. 1040 for the Holtec HI-STORM UMAX Cask Storage System (TAC No. L24664) Docket No. 72-1040, effective April 6, 2015 (excludes high seismic sites)
Underground systems are more likely to have overheating problems from wind affects than above ground cask systems.
- Impact of Variation in Environmental Conditions on the Thermal Performance of Dry Storage Casks, NRC NUREG-2174, Marcy 2016 Final (ML16081A181)
- See Appendix C for responses to public comments
- Impact of Variation in Environmental Conditions on the Thermal Performance of Dry Storage Casks, NRC NUREG-2174, February 2015 Draft (ML15054A207)
Holtec Transport Issues
NRC management approved Holtec’s high burnup nuclear fuel waste transport cask by ignoring NRC engineers’ critical safety concerns, NRC’s own evidence, and NRC’s transport regulations. It’s obvious from these actions NRC management cannot be trusted to protect our safety — which is the main purpose for their existence.
NRC Mission Statement: The NRC licenses and regulates the Nation’s civilian use of radioactive materials to protect public health and safety, promote the common defense and security, and protect the environment.
Cracked canisters cannot be safely transported according to NRC regulations. The below NRC regulation and Technical Specifications from the Areva NUHOMS high burnup transport cask make this clear.
- NRC Regulation 10 CFR § 71.85 Packaging and Transportation of Radioactive Materials. Preliminary determinations. Before the first use of any packaging for the shipment of licensed material — (a) The certificate holder shall ascertain that there are no cracks, pinholes, uncontrolled voids, or other defects that could significantly reduce the effectiveness of the packaging.
- NRC Certificate of Compliance [Areva] NUHOMS-MP197HB, Certificate 9302, April 23, 2014 (ML14114A099), Page 17, “For any DSC [Dry Storage thin-wall Canister] that has been used in storage, the condition of the DSC must be evaluated, prior to transportation, to verify that the integrity of the canister is maintained.”
In spite of this, the NRC approved the Holtec HI-STAR 190 Transport Cask using the Holtec Safety Analysis Report as their justification.
- Safety Analysis Report Holtec HI-STAR 190 Package (Revision 1), Holtec Report No. HI-2146214, June 8, 2017 (ML17166A448). The NRC used this document to justify the August 2017 approval of the Holtec HI-STAR 190 for high burnup spent fuel. The NRC is ignoring its own safety regulations with this approval. For example:
- Inspection for canister cracks or for canister content (damaged fuel, damaged fuel baskets) is not required before transport.
- The NRC knows there is no current technology that can inspect for cracks in canisters loaded with spent nuclear fuel, yet it approved this transport cask.
- The NRC knows Japan abolished use of aluminum alloy fuel baskets, yet does not require inspection of Holtec aluminum alloy (Metamic) fuel baskets. Baskets are needed to prevent a nuclear criticality “accident”.
- The NRC knows high burnup fuel assemblies can degrade after dry storage, yet does not require inspection of the fuel assemblies before transport.
- Unloading the canister at the destination location or elsewhere is not part of this Safety Analysis Report (SAR). Page 1.2-12 (Pdf page 32) states: Any further operations, such as unloading fuel assemblies from the MPC [Multi Purpose thin-wall canister] if that is required, and consideration of HBF [High Burnup Fuel] condition during unloading need to be performed under the jurisdiction of the location where the cask is unloaded, and is not part of this SAR.
- Inspection for canister cracks or for canister content (damaged fuel, damaged fuel baskets) is not required before transport.
- Holtec’s original application to the NRC for the HI-STAR 190 transport cask on August 7, 2015 (ML15219A582).
- This requires high burnup fuel and canisters to be intact prior to shipping in the transport cask. Holtec has no method to verify either condition.
- Transport system is heavier than all other transport cask systems with bounding loaded weight of 450,000 lbs (204 metric tons). Enclosure 2 to Holtec Letter 5024006, Response to Request for Additional Information, Holtec International, Docket No. 71-9373, HI-STAR 190 Transportation Package, August 30, 2016 (ML16238A214).
- NOTE: Thick wall casks storage/transport cask designs such as the Castor ductile cast iron cask, weigh 125 metric tons, meeting current transport weight requirements. The only other approved high burnup transport cask (Areva MP-197) weighs 137.7 metric tons.
- NRC states Holtec’s plan for transporting without adequate inspection for canister cracks and fuel assembly integrity is unacceptable in this Request for Additional Information (RAI). Response to 2nd Request for Additional Information, Holtec International, Docket No. 71-9373 HI-STAR 190 Transportation Package 2/26/2017 (ML17031A363)
Chapter 2 – Materials Evaluation, NRC RAI 2-1: Justify the adequacy of the proposed sampling process using MIL-STD-105 for reasonably demonstrating that MPCs [thin-wall canisters], with degraded conditions exceeding surface defects equal to or greater than 2mm depth, will be identified prior to transport.
In response to RAI 2-8, dated April 8, 2016, the applicant stated that the MPC enclosure vessel shell shall undergo a surface defect inspection prior to shipment to ensure that existing defects and flaws do not develop into cracks during hypothetical accident conditions of transport. The applicant further stated that this inspection may be conducted on the population of MPCs at an Independent Spent Fuel Storage Installation (ISFSI) using a statistical testing approach suggested in Military Standard MIL-STD-105E (1989) titled “Sampling Procedures and Tables for Inspection by Attributes”. The applicant clarified that not every MPC at a given ISFSI requires inspection.
However, the applicant did not provide a basis for the adequacy of the proposed standard guide for reasonably demonstrating that MPCs, with degraded conditions exceeding the proposed acceptance criteria, are adequately identified prior to transport.
This information is required to determine compliance with 10 CFR 71.71 and 71.73.
Chapter 7 – Package Operations, NRC RAI 7-1: Revise Chapter 7, “Package Operations”, of the application to clarify that the user must confirm that the analyzed configuration of stored high burnup fuel [HBF] has been maintained throughout the renewed storage period of the MPC prior to transport in the Model No. HI-STAR 190 package.
The application assumes that the configuration of HBF stored in an MPC during a renewed storage period (i.e. 20-60 years) has been maintained. Although age-related degradation of the fuel is not expected to compromise the configuration of the fuel during the renewed storage period, an Aging Management Program (AMP) is expected to be in place for providing confirmation to this effect (refer to Appendices B and D in NUREG-1927, Rev. 1).
Therefore, prior to transport in the Model No. HI-STAR 190 package, the user would be expected to confirm that the general licensee implementing the approved HBF AMP has not concluded that the analyzed configuration has been compromised during the renewed period of dry storage.
This information is required to determine compliance with 10 CFR 71.55(e), 71.73 and 71.85(a).
- Enclosure 2 to Holtec Letter 5024006, Response to Request for Additional Information, Holtec International, Docket No. 71-9373, HI-STAR 190 Transportation Package (ML16238A214), August 30, 2016
Bounding loaded weight 450,000 lbs [NOTE: higher than all other spent nuclear fuel assembly transport casks].
NRC RAI 2-8: Regarding MPCs previously in dry storage under a 10 CFR Part 72 license:
1. Revise the application to provide acceptance criteria for the MPC enclosure vessel integrity, which clearly defines allowable degraded conditions prior to transport. The acceptance criteria should demonstrate MPC containment integrity during hypothetical accident conditions.
2. Discuss methods (e.g. transport inspections) used to ensure that the MPC meets the proposed acceptance criteria.
The application (Section 8.2.1, “Structural and Pressure Tests”) states that the MPC maintenance program shall include an Aging Management Program (AMP) (under a 10 CFR Part 72 license) that verifies that the MPC pressure and/or containment boundary is free of cracks, pinholes, uncontrolled voids or other defects that could significantly reduce the effectiveness of the packaging. However, the application does not define acceptance criteria for other credible degraded conditions (e.g. loss of material due to localized corrosion pits, etching, crevice corrosion; presence of corrosion products) that ensures that cracks will not develop during transport, which could compromise the validity of the leak-tightness criterion during transport. The structural evaluation of the HI-STAR 190 package does not consider potential degraded conditions of the MPC during dry storage under a Part 72 license. Therefore, the application should describe the methods used to ensure that the acceptance criteria for the MPC enclosure vessel integrity are met. This could include pre- and post transport inspections that ensure that the safety analyses remain valid and the MPC is free of cracks, pinholes, uncontrolled voids, or other defects that could compromise the enclosure vessel integrity.
The staff notes that sole reliance on a Part 72 AMP is an overly-simplistic and inadequate approach, as the AMP may identify certain aging effects that the Part 72 licensee deems acceptable for continued storage following review under its corrective action program (CAP), but which could potentially compromise the MPC containment integrity during hypothetical accident conditions (HAC). For example, the acceptance criteria in the AMP for localized corrosion and stress corrosion cracking included in Appendix B of draft NUREG-1927, Rev. 1 (ML15180A011) states that any indications of localized corrosion pits, etching, crevice corrosion, stress corrosion cracking, red-orange colored corrosion products require additional examination and disposition under the Part 72 licensee’s CAP.
During the CAP review, the Part 72 licensee may use data from non-destructive examination and other analyses to support the conclusion that a given aging effect (e.g. loss of material due to localized corrosion pits, etching, crevice corrosion; presence of corrosion products) will not compromise the confinement function of the MPC for the expected loads during normal, off-normal and accident conditions of storage. Those loads, however, are not expected to be commensurate with HAC transport loads.
Therefore, reliance on a 10 CFR Part 72 AMP to assure compliance with the HI-STAR 190 structural safety analyses is inadequate.
This information is required to determine compliance with 10 CFR 71.55(e), 71.73 and 71.85(a).
Holtec Response to RAI 2-8:
We agree with staff’s position regarding the need for a higher level of confidence with respect to the MPC’s containment integrity under the § 71.73 free drop loading scenario than that assured by a Part 72-compliant Aging Management Plan. New Subsection 8.1.8 titled “MPC Enclosure Vessel Shell Surface Defect Inspection” has been incorporated in SAR Revision 0.C (provided with this RAI response) as a remedy to this matter with the following key commitments:
• MPC’s containing high burn-up fuel and stored beyond the duration of the initial 20 year license period under the provisions of 10CFR 72 shall undergo an MPC enclosure vessel shell surface defect inspection prior to shipment to ensure that existing defects and flaws do not develop into cracks during hypothetical accident conditions of transport.
• The MPC shall be subject to an Eddy current testing (ECT) regimen that is capable of identifying any surface defect equal or greater than 2 mm deep anywhere on the external cylindrical surface of the enclosure vessel.
• This test may be conducted on the population of MPCs at an ISFSI using a statistical testing approach suggested in Military Standard MIL-STD-105E (1989) titled “Sampling Procedures and Tables for Inspection by Attributes”. Not every MPC at a given ISFSI requires inspection.
• Any flaw that exceed 2 mm in depth will disqualify the canister for transport until further investigation is performed and the NRC accepts, under the exemption process or other appropriate licensing action, the owner-provided evidence that the affected canister will survive a HAC. Inasmuch as the ECT is considered the most definitive detector of cracks, pits and other types of surface flaws and is universally relied upon for detecting minute degradation in the tubing of critical nuclear plant heat transfer equipment such as Steam Generators, we propose to use this proven technology to determine the structural integrity status of the MPC’s.
[NOTE: Eddy Current Testing is inadequate to detect or measure cracks, despite what Holtec said above. For example, as stated in the following Parrott report:
The simplest and most effective NDE technique for detecting CLSCC [chloride stress corrosion cracking] is dye penetrant testing [which cannot be done in canisters loaded with nuclear waste]. Eddy Current Testing (ECT) is effective with purpose-designed probes that have been calibrated on known defects. ECT was found to be ineffective on the samples from the reactor due to limited penetration of the current and sensitivity to surface imperfections that could not be distinguished from cracking. Chloride stress corrosion cracking in austenitic stainless steel, Assessing susceptibility and structural integrity, UK, prepared by the Health and Safety Laboratory for the Health and Safety Executive, 2011 R Parrott, et. al., SK17 9JN. ]
We believe the above commitments provide a robust means to ensure that only those MPCs that have a structurally competent containment boundary to meet the transport accident of §71.73 will be transported in HI-STAR 190.
See Holtec response to RAI 2-12 for additional proposed changes to Section 1.0, Subsection 1.A.3.2, Table 8.2.1, Appendix A and Table 8.A.1 regarding this inspection. In addition, Section 7.0, Subsection 7.1.2, Subsection 7.1.3, Appendix 7.B have been revised to incorporate the surface inspection as appropriate
Holtec Transport System HI-STAR 190 Technical Specifications
- Application Request for a Certificate of Compliance (CoC) for Holtec’s Model No. HI-STAR 190 Type B(U) F Transportation Package, August 14, 2015 (ML15319A582.html)
- ML15219A588 – Holtec International – Submits Application Request for a Certificate of Compliance (CoC) for Holtec’s Model No. HI-STAR 190 Type B(U) F Transportation Package. (2 page(s), 8/7/2015))
- ML15219A589 – Holtec International – Certificate Of Compliance for Radioactive Material Packages for docket 71-9373. (4 page(s), 8/7/2015)
- ML15219A585 – Holtec International – Non-Proprietary Version Safety Analysis Report on The HI-STAR 190 Package (Revision 0). (582 page(s), 8/7/2015)
- ML15219A586 – Holtec International – Affidavit. (5 page(s), 8/7/2015)
Unresolved concrete degradation in Concrete Cask Storage Systems
NRC’s Expert Panel Workshop on Degradation of Concrete in Spent Nuclear Fuel Dry Cask Storage Systems, February 24-25, 2015, identified numerous concrete aging management problems, particularly with below ground systems (such as the Holtec UMAX dry storage system) due to limited inspection capability, ground moisture and chemical reactions with concrete. Concrete is not an issue in thick steel or ductile cast iron casks, since they don’t use concrete for gamma and neutron shielding.
- NRC Concrete Expert Panel Workshop, February 24-25, 2015
U.S. Utilities choose inferior steel/concrete canister designs due to cost even though even short-term costs will be higher with thin-wall canister systems.
- The vendors informed the committee that cost is the chief consideration for their customers when making purchasing decisions. Cost considerations are driving the cask industry away from all-metal [thick] cask designs and toward [steel/]concrete designs for storage. National Research Council of the National Academies (2006), Safety and Security of Commercial Spent Nuclear Fuel Storage, National Academies Press, Washington D.C., page 63.
- Cost-based case testimony and evidence (legal briefs) submitted to the California Public Utilities Commission (CPUC) by intervener Donna Gilmore and David Peffer. Judge Bushey ruled them “out of scope” even though the CPUC has regulatory authority over costs and even though she stated these were meritorious issues. The Nuclear Regulatory Commission regulates safety, not costs, so the CPUC is abdicating their responsibilities to the ratepayers on this issue.The Governor appointed CPUC Commissioners approved SCE’s Decommissioning plan in spite of evidence showing there are insufficient San Onofre Decommissioning Trust Funds, based on SCE’s Decommissioning Plan. SCE’s plan is based on unsubstantiated assumptions that nothing will go wrong and the federal government will remove the spent nuclear fuel waste in the short-term. Commissioner Florio set the scope of the hearing to exclude decisions about the dry storage system. However, the CPUC has the authority to require a cost/benefit analysis of this capital project and require they present additional options in that cost/benefit analysis.
Experimental UMAX System potential flooding problems
- The NRC admits the experimental nature of the UMAX cooling system and potential for flooding in their NRC Staff Evaluation of Responses to Requests for Additional Information for the Holtec International HI-STORM UMAX Canister Storage System Certificate of Compliance No. 1040, October 21, 2013 (ML13294A504)
The staff realizes that the applicant does not have experimental data obtained from a geometry that resembles the HI-STORM UMAX design. Unless the applicant can provide such validation in advance, the staff will issue the CoC at 80% of the total heat load being requested in the application. The staff determined that 20% reduction in the total decay heat will compensate for the uncertainties in the calculations and lack of experimental data to validate the analysis. In cases where data has become available, the staff has found that errors as large as 25% were associated with analytical results. The 20% reduction combined with the available margin in the vendor’s result would provide adequate justification for the thermal design. Once a cask is loaded to 80% of the design basis heat load, the applicant could perform the proposed test to obtain the necessary data which could be used to validate the analysis. At that point the applicant could amend the CoC for higher heat loads. These issues were discussed in an August 28, 2013, conference call with Holtec.
The applicant’s initial response to RAI 6-1, although very detailed, was insufficent to form a safety finding for the HI STORM UMAX storage system due to the potential for water to challenge the integrity of the MPC during a flood event and other credible sources. Additionally, the staff finds that Holtec has not provided acceptable contingency actions to address removing water from the CEC after incursion.
- Flooding risk: the Final Safety Analysis Report (FSAR) (ML14202A031) states on PDF Page 47 (I-21):
The essential design and operational features of the HI-STORM UMAX System are:… d. Removal of water from the bottom of the storage cavity can be carried out by the simple expedient use of a flexible hose inserted through the air inlet or outlet passageways.
- Gamma shielding: the FSAR states on PDF Page 48 (I-22):
184.108.40.206.3 Gamma Shielding
In the HI-TRAC transfer cask, the primary gamma shielding is provided by lead. As in the storage overpack, carbon steel supplements the lead gamma shielding of the HI-TRAC transfer cask.
In the MPC, the gamma shielding is provided by its stainless steel enclosure vessel (including a thick lid); and its aluminum based fuel basket and aluminum alloy basket shims.
Japan abolished use of aluminum baskets, but NRC and thin-canister vendors have not addressed this issue.
- The Japan Society of Mechanical Engineers abolished the aluminum alloy case standards of the metal cask structure standards on October 1, 2015. Summary of Decommissioning and Contaminated Water Management, December 24, 2015, by
Secretariat of the Team for Countermeasures for Decommissioning and Contaminated Water Treatment
- Holtec and other dry storage vendors also use aluminum baskets. However, the NRC, vendors and Southern California Edison have not addressed this issue.
- Unlike Japan and most other countries that have standardized on thick wall bolted lid casks, the majority of U.S. canisters are thin-wall and have welded lids. The only method to inspect the interior of the thin-wall canisters is to destroy these million dollar canisters.
- The NRC has continued to approved these thin-wall canisters that cannot even be inspected (inside or out), even though they know about the issues with the aluminum baskets.
Holtec HI-STORE Consolidated Interim Storage “UMAX” System
The HI-STORE system planned for New Mexico plans to double stack canisters in the Holtec holes in the ground.
- Holtec August 21, 2017 NRC Meeting
Diablo Canyon Holtec HI-STORM 100 above ground thin canister system
- Diablo Canyon Power Plant Independent Spent Fuel Storage Installation (ISFSI) Inspection Report and Notice of Violation, May 20, 2013
- Pacific Gas and Electric Company; Diablo Canyon Independent Spent Fuel Storage Installation Licence Issuance, Docket ID: NRC-2012-0312, February 19, 2014
- Diablo Canyon, Issuance of Materials License SNM-2511 for Diablo Canyon ISFSI (ML040780107), released July 13, 2005 contains links to technical specifications for Diablo Canyon’s HI-STORM 100 spent fuel storage system installation.
- Diablo Canyon NRC Event Notice #51134, not meeting technical specifications due to incorrect loading of casks, June 6, 2015: 17 of the 29 loaded casks in the Diablo Canyon ISFSI prior to the 2015 campaign were found to be out of compliance with ISFSI Technical Specification 2.1.2, Uniform and Preferential Fuel Loading. The casks were preferentially loaded based on heat load vs cooling time. On June 6, 2015, during a review of Independent Spent Fuel Storage (ISFSI) cask loading, plant personnel discovered that for two casks, preferential loading was not used during uniform loading as required by ISFSI Technical Specification 2.1.2, Uniform and Preferential Fuel Loading. “ISFSI Technical Specification 2.1.22 [ML040780229] requires that a preferential fuel loading configuration (i.e., that fuel assemblies with the longest cooling times shall be loaded into peripheral fuel storage locations) is used during uniform loading. [Fuel assemblies with shorter post-irradiation cooling times shall be placed toward the center of the basket.] Preferential loading was only partially met for two casks, designated MPC-253 and MPC-257. For these two casks, fuel assemblies with the longest cooling times were placed in the four center cask locations, which are only ones allowed for those assemblies containing control rods.
- Holtec directed or perform the fuel loadings. The 2013 NRC ISFSI Inspection report states Diablo Canyon plans to load approximately six casks every two years starting in August 2013. The removing of 96 assemblies (3 casks) from each pool will more than offset the 88 new assemblies being added to the pools every 20 months due to a refueling outage. The cask with the highest heat load to-date held 20.29 kW. NRC Diablo Canyon ISFSI Inspection 5/20/2013 (ML13140A430)
- Approved Holtec loading pattern requires longer cooling times for 20 fuel assemblies (Region 2). Only 12 shorter cooled fuel assemblies can be loaded (Region 1) in canister. Would Diablo Canyon have been able to keep operating if they had loaded the fuel correctly in the canisters?
Holtec International Contracts
- Holtec Awarded Contract for Supply of Dual-Purpose Metal Casks for Koeberg Nuclear Power Station in South Africa [HI-STAR 100].
- South African power utility Eskom is to pay an estimated ZAR200m ($15.6m) for seven new storage casks to keep its Koeberg nuclear plant running beyond 2018.
- The HI-STAR 100 is different than the majority of Holtec storage systems used in the U.S. It uses thin canisters, but stores them inside thick metal bolted-lid storage/transport casks designed for lower burnup fuel and requiring longer cooling times. The HI-STAR 100 allows 32-fuel assemblies (MPC-32). However, MPC-32’s are not allowed for damaged fuel assemblies. Holtec Safety Analysis Report HI-STAR 1000 Cask System, NRC Transport Docket 71-9261, October 11. 2010, Rev. 15.
- The HI-STAR 100 has only been licensed since October 1999.
Humboldt Bay HI-STAR 100HB casks
Humboldt Bay uses 5 HI-STAR 100HB casks for their 390 low burnup fuel assemblies, 95 of which are damaged. Each damaged assembly is placed in damaged fuel container [can].
Holtec Quality Issues
- Holtec Debarment and $12 million “administrative fee”, TVA 2013 Report, page 12
- In October 2010, TVA debarred Holtec International, Inc., based on the results of a criminal investigation.
- Criminal investigation by Department of Justice, August 3, 2007, Former TVA-BFN Manager pleads guilty to making false statement in connection with Financial Disclosure Form, Department of Justice, August 3, 2007
- On or about February 7, 2002, Symonds knew that USTD had been directed to send that $29,212.77 check to Krohn by Holtec International (Holtec) – a company that Symonds knew as of that time (1) had contracted with TVA in November 2001 to design and construct a dry cask storage system for spent nuclear fuel rods at TVA BFN and (2) had contracted with USTB to fabricate some of the construction materials for the TVA BFN dry cask storage system.
- Additionally, on or about February 27, 2002, during the reporting period for his October 21, 2002 OGE Form 450-A, Symonds co-owned Krohn Enterprises, LLC with his former spouse, and on or about February 27, 2002, Krohn Enterprises, LLC, was paid $25,000 by Check No. 31970 drawn on the Mellon Bank account of USTD. That $25,000 check was deposited into the Krohn Enterprises, LLC, Heritage Bank account, and the proceeds of that check were used to pay the personal expenses of Symonds and his former spouse. On or about February 27, 2002, Symonds knew that USTB had been directed to send that $25,000 check to Krohn by Holtec – a company that Symonds knew as of that time (1) had contracted with TVA in November 2001 to design and construct a dry cask storage system for spent nuclear fuel rods at TVA BFN and (2) had contracted with USTB to fabricate some of the construction materials for theTVA BFN dry cask storage system.
- U.S. Office of Government Ethics, DO-08-036: 2007 Conflict of Interest Prosecution Survey, November 6, 2008
- Case 12. The defendant was employed as a manager at the Tennessee Valley Authority’s Brown’s Ferry Nuclear Plant (TVA-BFN). He was required to complete and submit to TVA a Confidential Financial Disclosure Report, an OGE Form 450. He was required to submit an updated form annually. He was permitted to submit an OGE Form 450-A if there was no change in any of the information he had reported on the prior year’s form.On the form he submitted in November 2000, he answered “none” to the question that asked him to identify for himself and his spouse (1) any asset with a fair market value greater than $1,000 at the close of the reporting period or which produced income over $200 and (2) any non-Federal source of earned income such as salaries and fees over $200 during the reporting period. He certified that his statements were “true, complete, and correct to the best of [his] knowledge.”In October 2001 and October 2002 he submitted the OGE Form 450-A. On both forms he certified that there were no new reportable assets or sources of income for himself or his spouse and that neither he nor his spouse had any new reportable sources of income from non-Federal employment.Despite these certifications, in February 2002, during the reporting period for the October 2002 OGE Form 450-A, he co-owned Company D with his former spouse. Company Z issued 2 checks to Company D, one in the amount of $29,212.77 and the second in the amount of $25,000. The checks were deposited into Company D’s bank account and the proceeds of the checks were used to pay the personal expenses of the defendant and his former spouse. The defendant knew that Company Z had been directed to send the check to Company D by Company E. The defendant knew that Company E had contracted with the TVA in November 2001 to design and construct a dry cask storage system for spent nuclear fuel rods at TVA-BFN and had contracted with Company Z to fabricate some of the construction materials for the TVA-BFN dry cask storage system.The defendant knowingly and willfully failed to disclose on his confidential financial disclosure report that he had received, through Company D, either check.The defendant pleaded guilty to violating 18 U.S.C. § 1001, making a false material statement by executing and submitting an OGE Form 450-A on which he knowingly and willfully failed to disclose his receipt of $54,212.77 through Company D. He was sentenced to 2 years’ probation and a $5,000 fine.The Eastern District of Tennessee handled the prosecution.
- Office of the Inspector General, Tennessee Valley Authority, Semiannual Report, April 1, 2013 – September 30, 2013, Page 12
- Debarments – In 2010, TVA and the OIG worked collaboratively to develop a suspension and debarment process for contractors that defraud TVA. That same year, Holtec International, Inc. (Holtec), a dry cask storage system supplier for TVA nuclear plants, became the first contractor to be debarred in TVA history. Holtec’s debarment lasted sixty days. Also, Holtec agreed to pay a $2 million administrative fee and submit to a year-long monitoring program for its operations.
- Office of the Inspector General, Tennessee Valley Authority, Semiannual Report, October 1, 2010 to March 31, 2011 , page 8
- The OIG initiated a first in TVA history; the debarment of a contractor doing business with TVA. In October 2010, TVA debarred Holtec International, Inc., based on the results of a criminal investigation conducted by the OIG. Because of our recommendation, TVA created a formal suspension and debarment process and proceeded to debar Holtec for 60 days. Holtec agreed to pay a $2 million administrative fee and submit to independent monitoring of its operations for one year. The TVA Board’s Audit, Risk, and Regulation Committee and TVA management fully supported the OIG’s recommendation to create a suspension and debarment process and submit Holtec to that process. TVA’s Supply Chain organization and Office of General Counsel worked collaboratively with the OIG to achieve this milestone in TVA history.
- How does one contractor being debarred make life better for Valley residents? Ultimately, the less vulnerable TVA is to fraud the better chance rates stay low. This debarment signaled TVA’s commitment to do more than simply ask for the money back. This debarment action was literally heard around the world and drew a line in the sand. Yes, much of this was symbolic, but symbols matter when you are the largest public power company in America.
- More reports on TVA Holtec disbarment
- Contractor Misconduct Leads to First TVA Debarment and the Collection of $2 Million Administrative Fee, Page 35
- The OIG previously reported that a TVA technical contract manager received money from a TVA contractor. Criminal actions were taken against the former TVA technical contract manager in that investigation. In addition, a report of administrative inquiry was issued to TVA management regarding the actions of the contractor, Holtec International, Inc. In response to this report, TVA established and filled the position of a TVA suspension and debarment officer to review the matter, which led to the first debarment action at TVA. Holtec International, Inc., received a sixty-day debarment (October 12 through December 12, 2010); and, by agreement with TVA, will pay a $2 million administrative fee to TVA; appoint a corporate governance officer and an independent monitor (at the contractor’s expense); implement a code of conduct, to include training for all employees, executives, directors, and officers; add three noncompany members to its board of directors and sign an administrative agreement ensuring compliance to the above terms.
- Reports of Holtec quality control issues brings in to questions how reliable these casks will be over time.
Oscar Shirani alleges that all existing Holtec casks, some of which are already loaded with highly radioactive waste, as well as the casks under construction now , still flagrantly violate engineering codes (such as those of the American Society of Mechanical Engineers [ASME] and American National Standards Institute [ANSI]), as well as NRC regulations. He concludes that the Holtec casks are “nothing but garbage cans” if they are not made in accordance with government specifications.
Although NRC has dismissed Shirani’s concerns, NRC Region III (Chicago office) dry cask inspector Ross Landsman refused to sign and approve the NRC’s resolution of Shirani’s concerns, concluding that this same kind of thinking led to NASA’s Space Shuttle disasters. He stated in September 2003, “Holtec, as far as I’m concerned, has a non-effective QA program, and U.S. Tool & Die has no QA program whatsoever.” Landsman added that NRC’s Nuclear Reactor Regulation division did a poor follow-up on the significant issues identified, and prematurely closed them.